To fireplace amount W27x114 columns I would decide on an insulating board technique. The boards will be mounted to produce a hollow portion about the I-beam. The wallboard will be hooked up to the steel beam however have an air place concerning the board and the beam on all sides. The wallboard content is a fireplace resistant content to safeguard the column, while the air place will cut down thermal conductivity, hence growing the fireplace rating. As opposed to concrete the wallboard is light-weight and has a decreased thermal conductivity. As opposed to spray fireplace resistant content, the insulating board technique is a much better aesthetic choice as the columns may well be exposed in the unsprinklered spot. The cause I chose a box casement for this column is mainly because it utilizes significantly less gypsum and appears to be like much better than an I-portion casement while reaching the exact same fireplace rating.
The elements preferred to achieve this style and design are kind c gypsum board, cold fashioned steel clips, and corner beads. In order to get to a two hour fireplace rating, the nominal thickness of the gypsum mixed with the attachment of the casing need to meet up with certain specs. Before gypsum is hooked up the steel clips need to be hooked up to the flanges of the I-beam. On just about every conclude of the two flanges clips need to be hooked up to the steel so the spacer is facing the exterior of the beam in order to produce an air place on the flange sides. The clips will be positioned each individual four ft beginning at the base and doing the job up to the ceiling. Dimensionally, the clips must be roughly 1.five” deep in order to produce a massive plenty of airspace to achieve two hour fireplace rating and permit area for screwed connections. The kind c gypsum requires to be hooked up to the clips with self taping screws. Two levels of five/eight” wallboard requires to be hooked up all about the body of the I-beam created by the clips. The total wallboard thickness will be 1.25″. To complete exposed corner joints, corner beads will be nailed to the gypsum.
To assure fireplace rating this style and design has been as opposed to specs of skilled UL styles. Underwriter Laboratories has analyzed distinct products to be skilled for this style and design.
Source by Protechwood